RAH – RecoAir by Halton – Recirculating kitchen extract unit (UL)
No requirement for route to the atmosphere for all electric catering equipment
RecoAir by Halton RAH recirculating kitchen extract units work at the heart of a kitchen ventilation system serving all electric catering equipment and achieving complete recirculation of exhaust air with no requirement for ductwork to outside.
RAH units’ highly efficient filter technology removes particulates and odors. The processed air is independently certified as clean to be re-introduced as supply air.
Halton RecoAir RAH units eliminate long ductwork needed to go outside when they become too costly or when they simply are impossible to install. Technical constraints on buildings’ structure, restrictions linked to listed activities or historic sites, co-ownerships opposed to the degradation of the facades aesthetic or to odor nuisance risk… all these challenges can easily be overcome with recirculation units.
3 sizes available up to 3800 CFM capacity allows the RAH to serve hood lengths totaling almost 18 feet of Capture Jet with no limitations on the electrical appliances’ input power.
In addition to providing opportunities to install kitchen operations in previously unfeasible locations, RAH units significantly reduce fire risk. They also simplify planning procedures.
Globally Cost Effective
RAH units reduce CAPEX investment. They eliminate the costly fire-rated ductwork to the atmosphere thus reducing the construction and installation costs.
They also reduce the utility usage and plant requirement with a compact design, ease of assembly, and flat pack options.
RAH units enable establishing a restaurant wherever you chose i.e. where it is of most value, whatever the technical or environmental challenges.
Traditional extract ductwork requires regular specialist cleaning. RAH units significantly reduce maintenance regimes when accessing duct systems and plant is difficult and time consuming.
Reduced Fire Risk and Emissions Control
RAH units significantly reduce fire risk by eliminating ductwork to outside and suppressing grease deposits after the unit.
RAH units reduce the need to pierce buildings’ fire compartments.
RAH units can be installed in a fire-rated enclosure. Whether located inside or outside the main hazard area, the risk is minimized.
The contaminants produced by commercial kitchens are no longer expelled to outside thus removing the risk of nuisance on the neighborhood and possible legal actions.
Distant Monitoring ( Optional)
Equipped with Halton Connect IoT (Internet of Things) platform with advanced 24/7 distant monitoring capabilities.
Highest value of ownership thanks to Halton Connect & Care smart services offering.
Air Cleanliness Study by Validair.
Acoustic survey report by Applied Acoustic Design.
Ceiling Void Units
RAH Reco-Air recirculating kitchen extract unit
The recirculating extract unit shall be Halton Brand, Reco-Air by Halton RAH range. It is equipped with a full air treatment system to remove grease, steam, smoke and odors from the extract air.
The unit shall be supplied complete, fully pre-wired from factory, and ready to be installed. The following specifications shall be fully observed.
General Unit Construction
Unit shall be constructed of 25 mm double walled, galvanized steel panels with internal and external powder coat finish. They shall be insulated using 45 kg/m3 density mineral wool to ensure good acoustic performance & thermal properties.
Access doors to the main filter sections shall be lift off or mounted on hinges, equipped with lockable black handles for an access by Authorized Personnel only. Fan(s) access door(s) shall be screwed.
As a minimum requirement, each unit shall incorporate the following grade filter media:
– Coarse 60-70% (ISO 16890) – Large grease particulate removal.
– ePM2.5 50% to coarse 85% (ISO 16890) – Fine grease particulate removal.
– E10 85% MPPS (EN 1822) – Smoke removal.
– Food Grade Activated Carbon cylinders – Odor removal minimum dwell time shall be 0.2 seconds.
As a minimum requirement, each unit shall incorporate the following fan assembly (voltage to be verified when sending for review):
– EC Plug fan, 230 or 400 V (depending on unit capacity).
– Single / Three phase, suitable for 0 to 10V signal control.
– Unit Duty to suit current DW/172 Specific Extract Flow Rate (SEFR) or supplier’s recommendation when applicable as well as design requirements.
– Max. ambient working temperature to suit specific applications.
– Each fan shall be Inverter Controlled, so fan speed ramps up as the filter pressure increases to maintain a constant air volume flow rate at the cook line/hood.
RecoAir unit to be factory supplied with complete wet chemical fire system compliant with U.L. 300 standards. The system shall include factory pre-pipe, tanks, regulators, and fusible links. Automatic actuation shall be by means of fusible link rated for the cooking duty. The system shall be furnished and installed by a certified distributor in accordance with the manufacturer’s instructions and the authority having jurisdiction.
Microswitches shall be furnished as part of the fire protection system for tie in of building alarm and for make-up air/fire/fuel shut down. Shunt trip breakers by others.
If applicable, the Building Alarm System Contractor is to furnish a control relay to detect the operation of the system by connection to the microswitches supplied. The Electrical Contractor is to furnish and install all wiring required for the system specified.
Control platform & Interface Requirements
The control platform shall include a unique LCD user interface common to all technologies of the manufacturer.
Optional Halton Connect shall also have advanced distant monitoring capabilities enabling future premium services, including predictive maintenance of the systems.
The control platform shall ensure the unit ceases to function if any of the following scenarios arise:
– A unit filter access door is left open or slightly open.
– Filters are removed or left out of the unit.
– The Fire Alarm system is activated.
– The registered filter pressure drop across any of the primary 3 sets of filters exceeds pre-set warning levels & reaches critical levels.
– The unit Isolator is turned Off.
– A system Timeclock – external controls – is not calling for system activation.
– A remote Shut-off safety feature – external controls -has been activated.
An electrical interlock system shall be incorporated to disable all essential cooking equipment whenever a ‘No Air Flow’ status is present.
Air Commissioning / Testing
The unit(s) shall be delivered pre-commissioned from the factory.
On completion of any RecoAir unit installation, the air volume flow rates to extract & return air ductwork must be verified by a suitably qualified commissioning engineer & a report produced as point of record.
All test points are sealed with proprietary plugs on completion of this operation.
Measures for unit’s Service & Maintenance
When planning the installation of the recirculation unit –however configured – adequate clearance must be allowed to facilitate safe operative replacement of the filter media & fan(s).
To comply with Specific Landlord / Authority approvals – a Service Contract is required. It is highly recommended to use a suppliers’ accredited service partner.
Evidence of same must be made available prior to formal approval being acknowledged.
Reco-Air Unit Noise Breakout
In normal ‘Internal’ instances, breakout noise from the unit shall not exceed 60 dB(A) when measured at 1 metre (free field).
Where Specific Authorities enforce lower noise levels, the unit construction shall be modified accordingly.